Jiangsu Aoguang Corrugated Pipe Co.,Ltd
Address:Shuguang industrial park jiangyan taizhou city jiangsu province China
Large Horizontal Rod Compensator
Compensator installation and use requirements: 1, the compensator in the installation should first check the model, specifications and pipeline configuration, must meet the design requirements. 2, the compensation of the sleeve with the sleeve should pay attention to the direction of the sleeve...
Compensator installation and use requirements:
1, the compensator in the installation should first check the model, specifications and pipeline configuration, must meet the design requirements.
2, the compensation of the sleeve with the sleeve should pay attention to the direction of the sleeve and the direction of flow media, hinge compensator hinge rotation plane should be consistent with the displacement of the rotation plane.
3, the need for "cold" of the compensator, pre-deformation of the auxiliary components used in the pipeline should be removed before the end of the installation.
4, the corrugated compensator deformation method is strictly prohibited to adjust the pipeline installation tolerance, so as not to affect the normal function of the compensator to reduce the service life and increase the piping, equipment, supporting the load components.
5, the installation process, do not allow welding slag splash to the surface of the wave shell, does not allow wave shell by other mechanical damage.
6, after the installation of piping system, as soon as possible after the removal of the bellows compensator for the installation and transportation of yellow auxiliary positioning components and fasteners, according to design requirements will be transferred to the specified limit device position, the pipe system under environmental conditions Adequate compensation capacity.
7, the compensator all the active components shall not be stuck outside the external components or limit the scope of its activities, should ensure that the activities of the normal activities of parts.
8, the hydraulic test, should be equipped with compensator pipe end of the sub-fixed pipe rack reinforcement, so that the pipeline does not move or turn. The compensator for the gas medium and its connecting pipe, pay attention to whether the need for additional temporary water scaffold. Water pressure test water cleaning fluid 96 chlorine ion content of not more than 25PPM.
9, after the end of hydrostatic test, wave shell should be as soon as possible row of water, and quickly wave shell inside the surface dry.
10, and the compensator bellows contact with the insulation material should not contain chloride ions.
With the aid of wide experience and expertise, AOGUANG is an ISO9001 certified company specialized in large horizontal rod compensator. As one of the leading manufacturers and suppliers in China, we warmly welcome you to get buy the quality and precise stainless steel hoses made in China from our factory.