Jiangsu Aoguang Corrugated Pipe Co.,Ltd
Address:Shuguang industrial park jiangyan taizhou city jiangsu province China
1, the Compensator Series Series Series Series should be installed before checking its model, specifications and pipe configuration, must meet the design requirements.
2, the Compensator Series Series Series Series on the sleeve should be noted that the direction of the inner sleeve and the media flow direction consistent with the hinge Compensator Series Series Series Series hinge rotation plane should be consistent with the displacement rotation plane.
3, the need for "cold" Compensator Series Series Series Series, pre-deformation of the auxiliary components used in the pipeline after the installation can be removed.
4, it is strictly prohibited to use the corrugated Compensator Series Series Series Series deformation method to adjust the pipeline installation tolerance, so as not to affect the normal function of the Compensator Series Series Series Series, reduce the service life and increase the pipe system, equipment, support components of the load.
5, the installation process, does not allow the welding slag splash to the surface of the wave shell, does not allow the wave shell by other mechanical damage.
6, after the installation of the pipeline system should be removed as soon as possible on the corrugated Compensator Series Series Series Series for the installation and transportation of the yellow auxiliary positioning components and fasteners, according to the design requirements of the limit device transferred to the specified location, the system under the environmental conditions Full compensation capacity.
7, Compensator Series Series Series Series All active components shall not be stuck or restricted by the external activities of its range of activities, should ensure that the activities of the normal operation.
8, water pressure test, should be equipped with Compensator Series Series Series Series tube end of the secondary fixed pipe rack reinforcement, so that the pipeline does not move or turn. For Compensator Series Series Series Seriess for gas media and their connecting lines, it is important to note whether additional temporary brackets are required for water filling. Water pressure test water cleaning solution of 96 chloride ion content of not more than 25PPM.
9, after the end of the hydraulic test, should be as soon as possible in the wave shell in the water, and quickly spread the inner surface of the wave shell.
10, with the Compensator Series Series Series Series bellows contact with the insulation material should not contain chlorine.
Compensator Series Series Series Series with rectangular cross-section, rounded corners, a single expansion joint in the pipeline to bear the two-dimensional displacement. The elbow ducts, which consist of two expansion joints, are capable of withstanding three-dimensional displacements. Rectangular fillet metal corrugated expansion joints are full height, semi-high, according to the flue size, stress and strain requirements of the user can be multi-band selection.
1, the user according to the heat transfer of the pipe system after the selection of a suitable Compensator Series Series Series Series, at least have to provide the tube in the circulation medium, smoke duct design pressure, the maximum operating temperature, smoke duct cross-sectional dimensions (length (Wide) height of the selected waveform (full height 216mm, half height 108mm) and the number of waves (single ripple single wave number of not more than 6 waves), in order to carry out the structural design and manufacture of the Compensator Series Series Series Series.
2, the maximum allowable expansion of each wave: full height △ α = ± 24mm semi-high △ α = ± 12mm.
3, the blockboard: the duct or less dust pipe can not be used, the dusty flue should be used to play gray plate.
4, in order to reduce the number of bellows, should be considered cold pull 50%.
5, the Compensator Series Series Series Series for cross-sectional area of less than 4.6 square meters and smoke duct surface size is less than 1.5m but greater than 0.6mm of the occasion. The standard full height corrugated Compensator Series Series Series Series is suitable for all smoke ducts.
- Damper For A Brief Introduction
- Compensator Simple Overview
- Compensator Selection Techniques
- On The Question Of Selection Of Com...
- Compensator For Reliable Research
- Compensator Durability Test
- Main Functions Of The Expansion Joint
- Expansion Joint Structure
- Overall Design Of Expansion Joint
- Control Points Of Expansion Joints
- Expansion Joint Reduce The Deformat...
- Stainless Steel Chimneys Must Be Re...
- Damper Reduce The Shortcomings Of P...
- Bearing Good Dimensional Stability ...
- Expansion Joint A Traditional Proce...
- Damper Make The Piano Sound More Crisp
- Bearing Increased Plant Productivit...
- BBD Blast Furnace Dehumidifier To E...
- BBD Blast Furnace Dehumidifier Alwa...
- Bearing With A Simple Structure, Ea...